Regulators ZSN1 are used to control preset pressure in process installations connected to regulator valve outlet. Regulators are applied in heating systems, in industrial processes with cold and hot water, steam, air and nonfl ammable gases. Using with other media subject to consulting with manufacturer.CONSTRUCTION:
Regulator comprises three, temporary fastened main units: valve (01), actuator (02) and adjuster (03). Regulator valve single-ported with balanced plug. Flanged connections of valve body with valve face as per PN-EN 1092-1:2006 and PN-EN 1092-2:1999 for PN10; 16; 25; 40 PN-EN 1759-1:2005 for CL150; CL300. Diaphragm actuator (diaphragm effective area 80 cm2), with clammed housing, or diaphragm actuator (diaphragm effective area 160 cm2), with bolted housing. Control pressure value adjuster with combination of three pre-tensioned springs, fi xed coaxially with valve and actuator.